The MR-0152 submodule enables the connection of the TECOMAT TC700 PLC to the PROFIBUS DP network as a slave station with a transfer rate of up to 12 MBd. It can only be used in PCB mode.
Due to the fact that the physical interface of the PROFIBUS bus corresponds to the RS485 standard, the connection of the serial channel connector is the same as when fitted with the MR-0112 submodule (see Tab.22.214.171.124), including the termination option.
The MR-0152 submodule is supported by CP-700x central units from sw version 5.0. The hw version must be 02.